TECH | The Different AC Motors Used in HVACR Systems
July, 24th 2017 Comments Views
to the rising population and growth of commercial and industrial units
in the Middle East and North Africa, the demand for HVACR products in
the region remains high for different applications including commercial,
industrial, and residential among others. To be able to supply the
needs of these industries, HVACR companies make sure to develop high
One of the most important products in the HVAC industry are the electric motors. It is the basic component that is responsible for powering blowers to move air. Electric motors drive compressors to compress refrigerants and also powers pumps or chilled and hot water applications. It is an integral part of all HVAC systems, and many applications would not be possible to implement without electric motors.
The type of motor that is used in HVAC systems depends on its application. For example, electric blowers or propeller fans usually require motors that have a low starting torque, while compressors require motors that have high starting torque. This is why it is important for HVAC engineers to select the appropriate motor of the job, else problems will occur throughout the operation of the HVAC system.
Here are the different AC motors that are used in HVACR Systems.
Split Phase Motors
motors are known as the workhorse in the HVAC industry, they are
usually used in air conditioners because these motors provide high
starting torque. There are two common split-phase motors that are used in
HVAC applications, the capacitor-start-induction-run motor and the
resistance-start-induction-run electric motor.
Capacitor start motors make use of a start capacitor to boost its starting torque. Most of these motors use a centrifugal switch to disconnect the start capacitor from the start winding circuit at the time the motor will reach around 70 to 80 of its run speed.
resistance-start-induction-run electric motor on the other hand, has a
start winding and a run winding. The two windings are out of phase by 45
to 90 degrees which gives the motor a boost on startup. Unlike the
capacitor-start-induction-run motor that used a capacitor, this motor
makes use of a centrifugal switch to drop the start winding out of the
Permanent Split Capacitor (PSC) electric motors have many HVAC applications. They are used for many refrigeration and air conditioning compressor applications. These motors, are single phase electric motors. They are easily reversible from the clockwise to counter-clockwise direction. The PSC motor uses a capacitor and has good running efficiency.
a PSC motor is used in compressors, it makes use of two capacitors
attached to its wiring. The first one serves as a start capacitor to
boost the starting torque, and the second is a run capacitor to increase
its running efficiency.
Shaded-pole Electric Motor
Shaded-pole electric motors in the HVAC industry, are usually used only for application fractional horsepower applications wherein the start and run torque requirements are minimal. These motors are used in devices with low starting torque such as electric fans and small pumps. Shaded-pole electric motors do not use capacitors and are not easily reversible.